MTL FS32 Surge Protector
Prevents surges and transient over-voltages conducted along the Trunk or Spurs of fieldbus systems from damaging electronics
Mo-Th 8am to 5:30pm. Fr 8am to 5pm ET
- Protects intrinsically safe spurs
- On MTL 937x-FB range fieldbus
- 20kA maximum surge current per line
- Working voltage: ±32Vdc
- Limiting voltage: 62V @ 3kA 8/20μs
- EMC compliance: BS EN 61326-1:2013
- Electrical Safety: BS EN 61643-21:2001
- Plug connectors for quick & easy connection or rewiring
- Meets the requirements of IEC61158-2:2004
The MTL FS32 surge protector prevents surges and transient over-voltages conducted along the Trunk or Spurs of fieldbus systems from damaging the associated electronics such as terminators, spur blocks and the bus control equipment. Designed to fit Eaton's latest MTL fieldbus barrier product to protect spurs the FS32 can also be used to protect spurs on Megablock wiring hubs. This space saving design helps to reduce the size of junction boxes and ease installation.
The multi-stage hybrid surge protection network at the heart of the FS32 uses a combination of solid state electronics and a gas-filled discharge tube (GDT) to provide surge protection up to 20kA. This impressive surge protection circuit is design to exhibit exceptionally low line resistance and has negligible voltage drop to the spurs.
In operation the FS32 does not adversely affect the performance or operation of the fieldbus or connected equipment, it allows signals to pass with little attenuation while diverting surge currents safely to earth (ground) and clamping output voltages to safe levels.
Fully automatic in operation the FS32 devices react immediately to make sure that the equipment is never exposed to damaging surges between lines or the lines to earth (ground). Reacting instantaneously the FS32 redirects surges safely to earth (ground) and then resets automatically.
The MTL FS32 represents the next generation of surge protection to be fitted on Foundation™ fieldbus Systems. The space saving form factor allows the FS32 to be connected directly to the terminal receptacle on the module carrier of the 9370 fieldbus barrier. The earth (ground) is connected through the mounting screw in one simple operation. The field spur cable termination block plugs directly into the FS32 allowing fast and effective retro fitting if desired with no additional hardware being required.