Fisher R130 Changeover Manifold Assembly
Up to 1,475,000 BTU/hr, 1/4in NPT inlets LP-gas up to 250 psi and changes from supply cylinder to reserve if gauge drops below 35 psi
Mo-Th 8am to 5:30pm. Fr 8am to 5pm ET
- 250 psig (17.2 bar) maximum inlet pressure
- Standard outlet setting is 45 psig (3.1 bar) for supply
- 30 psig (2.1 bar) for reserve
- Propane flow capacities up to 1,475,000 BTU/hr
- 1/4in female NPT inlet and outlet connections
- -20 to 160°F (-29 to 71°C) operating temperature
The Fisher R130 changeover manifold assembly consists of two 67C series regulators and a special 0 to 60 psig (0 to 4.1 bar) pressure gauge. The gauge serves as the changeover indicator; it's painted red from 0 to 35 psig (0 to 2.4 bar) and when the dial reads in the red range it indicates that the manifold has switched from the supply to the reserve cylinder.
This unit is intended for use with second-stage regulators and/or separate relief devices which provide overpressure protection required by NFPA 58. Capacity of all changeover manifolds is dependent on the size of the second-stage regulator with which they are used. If the manifold is used as a final-stage (pounds-to-pounds), a relief valve is required in the downstream system. WARNING: Failure to follow these instructions or to properly install and maintain this equipment could result in an explosion and/or fire causing property damage and personal injury or death.
Fisher equipment must be installed, operated and maintained in accordance with Federal, state, and local codes and Fisher instructions. Only personnel trained in the proper procedures, codes, standards and regulations of the LP-gas industry should install and service this equipment.